What is proportional pressure control? Proportional pressure is a control method for variable speed pumps which results in reduced pump energy costs. It is a control mode that simply reduces pump head proportionally with flow. This type of control is very common in closed system heating and cooling applications, commonly configured in Primary/Secondary or secondary pumping systems where the liquid is pumped to heating/cooling coils or air handling units with modulating control valves.

The Grundfos Hydro MPC system controller (CU352) can provide proportional pressure control in different ways. The simplest way is to use the inlet and outlet sensors that are factory mounted on the manifolds. The CU352 controller will simply do a subtraction to determine the differential pressure. Alternatively, a differential pressure transmitter can be factory supplied if that is desired. The pump curves (5th order polynomial) are loaded into the control as well as the power curves. The CU352 controller can then determine the approximate flow rate at any speed. As flow changes, the pump speed will be adjusted accordingly to follow the appropriate control curve. The control curve with either be proportional pressure (Linear) or Quadratic pressure (a.k.a. Squared) as shown in Figure 1.

When the header sensors are used, you’ll need to set up the Proportional Pressure to Enabled. You will choose Linear or Square (Square = Quadratic). The [influence at 0 flow] setting defines the control curve head at zero flow.
So, for example if our total head is 60 feet and our minimum control head is 30 feet, the influence at zero flow is 30/60 or 50%. The last setting for Proportional Pressure is where you define the high flow end of the control curve. If the [Use pump curve] box is checked, the control curve will cross the full speed pump curve at 60 feet of head. If the [Enter value] box is checked, the control curve will start at 60 feet of head and the specific flow rate that is entered [Qpmax]. This allows the user to have a very well-defined control curve.

An example of this control curve (solid red) starting at 1500 gpm/60 feet is shown in Figure 7. The dashed control curve below would be the result of checking the [Use pump curve] box in the Proportional Pressure setting as this curve intersects the full speed pump curve at 60 feet.

What else can we learn from Figure 7?

1. This pump curve shows 3 parallel connected pumps. The control curve can be set to go across any number of pumps. For example, of one pump was a backup pump the control curve could start at 1000 gpm.
2. Pump 2 and pump 3 both start at 71% speed. Most VFD pump controls will start additional pumps based on a preset speed or frequency (95% or 58 Hz etc.). The Grundfos CU352 controller will stage pumps based on efficiency. You will notice that the efficiency drops to below 70% at around 390 gpm. With both pumps 1 & 2 in operation between 390 and 740 gpm, the pump efficiency stays between 74 and 76%. Then at 740 gpm the third pump is started, and the efficiency once again increases.

Communication to the Building Management System

Hydro MPC systems can be supplied with communication capability to a Building Management System (BMS), the most common protocols being BACnet MS/TP, BACnet IP, LON, Modbus RTU and Modbus TCP.

1. The Primary Sensor must be connected to the Hydro MPC via analog signal (4-20mA or 0-10V).
2. The system set-point can be adjusted via an analog input or through the BMS. If for example BACnet is used, the setpoint will need to be configured in percent of the feedback sensor range. If the feedback sensor is 0-145 psi and the setpoint is 13 psi for example, the setpoint from the BMS will be 8.9% (13/145 = 0.089 or 8.9%). Alternatively, the BMS can be set up to output an Analog signal of 4-20mA or 0-10 volts. The CU 352 would then be set up for an external influence that reduces the setpoint by a percentage. In this case the influence would reduce the local setpoint according to the analog input percentage. For example, if the local setpoint was 15 psi but a 13 psi setpoint was desired and the analog signal type was 4-20mA, the signal would need to be at 86.7%
(13/15 = 0.867). There are 16 mA between 4 and 20 therefore the signal would need to be 86.7% of 16 added to the 4. Therefore, to achieve a 13 psi setpoint the signal would need to be 17.9 mA [ (0.867 x 16) + 4 = 17.9 ]

Secondary Sensor

Another key feature of the CU352 is the secondary sensor. If the Primary sensor signal is lost, the Hydro MPC can revert to the header sensors until the primary sensor signal is restored. An example of this would be if the
remote dP signal is lost, the header sensors will take over, maintaining a differential or proportional pressure across the pumps until the remote dP sensor signal is restored.

Special thanks to Ed Sullivan from Urell Inc. for creating this educational document. For additional information or to schedule a training class, contact your local Grundfos rep agency.